Cost to move an electrical panel
Posted October 27 2009 - 08:34 AM
My wife and I are toying with the idea of opening up our kitchen, dining room, den, and utility room into one big great room. One of the issues that we have is that the main circuit panel is on an interior wall, and would be very much in the way of our plan.
So, I'm sure that it's a pretty big job, but how big of a job is it to move the main circuit panel? Would the cost be effected by how far it was moved? We could move it just to the other side of the doorway where it is now (about four feet away from its current location), or move it into another part of the house (say 20 feet away). I'm not sure if the distance has a major effect on the cost or not.
Posted October 27 2009 - 09:52 AM
I think a lot would depend on the service to the house(amount of amps). However, I do not think it would be that much. The bonus here is that there will likely be a LOT of sheet-rock work done, and ripping a big hole in one to run wiring and what not would not be that big of a deal, as long as you mount it in the already-being-renovated area.
The wire is expensive, so keeping the length of wiring extensions minimal will keep your costs down somewhat. Biggest issue is seeing where it "can" go w/ regards to codes.
Posted October 27 2009 - 01:29 PM
Posted October 27 2009 - 03:28 PM
You can no longer have an electrical panel in a cabinet, broom closet or above a counter.
Posted October 27 2009 - 05:04 PM
I wrote this a few months ago;
On my house here in NC, I wanted to build a garage to store my trucks & camper in, I had to re-locate a 400Amp service. Included in the job was reconfiguring one panel to serve a 200Amp transfer switch for a 20K water cooled propane generator and relocate the meter for the 400A service. The code had changed here which required main disconnects for each panel located outside & accessible to the fire dept. While the new garage was being built, we had to run the house of a 400A temp service.
So relocate 2 200A panels, install 2 main disconnects, install 1 200A transfer switch with a picky inspector (small town) plus we were living in the house, so everything had to work at the end of each day. I was also recovering from 2 major back surgeries done days apart. Doing this would require abandoning conduit runs to and from the temp service, while reusing the wires, as they were going to be under the slab floor.
The inspector required us to have a junction box for each wire amperage, 15A, 20A, 30A, 40A, 50A, 60A. He would not allow just a couple of big splice boxes for it all. He would not allow double romex connectors. The contractor fought hard to not abandon conduit, I was paying, what did it matter.
All the junction boxes had to go into the garage ceiling, which is a fire rated ceiling, thatâ€™s the reason I didnâ€™t like so many boxes.
Now about relocating a service for cosmetic reasons; The abandoned fuse or circuit breaker box, canâ€™t be used as a splice box, each and every splice has to be readily accessible. A route from the splice boxes to the new main breaker box will have to be figured out. The best one could end up with is a wall full of splice boxes instead of one big breaker box. Some wires might not be long enough to get into a splice box with itâ€™s brother so there could be splice boxes in the ceiling near where the old breaker box was.
It is not cheap to relocate a service, before I hired an electrician, I would hire one or several interior decorators, to deal with the problem in a more creative fashion. The box can be hidden by drapes, artwork or faux doors.
Posted October 27 2009 - 05:12 PM
Posted October 29 2009 - 06:38 AM
Cost about $1200. They had to add a bunch of junction boxes in the attic to extend the runs. My box is on the end of the house.
If you're going to move it, upgarade to 200.
If you can, try to get the box closer to the main loads (or a central location). This will save a little $ because of less I squared R loss.
Posted October 29 2009 - 12:30 PM
I squared R ...used to do that stuff in my sleep 7 years ago...did you have to get a new meter outside also? Who did you get to do it?
Posted October 29 2009 - 12:35 PM
about 3 yrs ago had a panel replaced in a house in PA.
was about $1000.00
figure NJ being a little more,
add in extra costs for extra possible work, depending on exact work you require.
Posted October 30 2009 - 03:29 PM
Posted October 31 2009 - 11:01 AM
Thanks for all of your input. It really helped me to figure out that moving the box is a no-brainer for what we want to do. The box is on a wall that splits our utility/laundry room from our den. We want to get rid of that wall, in order to open up the house. I was thinking that moving the panel is such a big job, that we would have a small wall in the way of otherwise open space. It doesn't look like that will be the case after the information that you all provided me.
You all rule.
By the way, I may change my screen name from doyle007 to "I squared R". I have absolutely no idea what it means, but it sounds cool.
Enjoy your weekend.
Posted July 28 2014 - 02:13 PM
My home is located in CA and was built in 1962. The original panel/fuse box (not sure of terminology) is now located in my walk in closet after a remodel done many years ago. It also seems like it's not in the best condition. The fuses trip more than they used to and now are more difficult to press in to show ON. I want to move outside (not sure sure about code but I think that having the box in a closet with clothes, etc. could be a fire hazzard). I see that distance is a factor for cost of wire, correct? I think it would have to be moved 10-20'. Please let me know what the cost might be and any other advice. Thank you!
Posted July 30 2014 - 09:50 AM
Posted July 30 2014 - 10:03 AM
I figured as much. I just want to find a good one and not get overcharged. Any idea about how much something like this would cost in CA or better yet have a suggestion for a good source to find one? Yelp? Thanks for responding!
Posted July 31 2014 - 03:15 PM
They should be able to give you a free estimate. It will probably be over 2K. It sounds like you should re-locate the panel and install a couple new circuits to handle your load.